DeltaV KL3002X1-BA1 | 8-CH High-Side Digital Output Module

2026-04-10T11:23:08+08:00

Vendor: Emerson
Type: DeltaV M-Series
Price: 199.00

Product Details

Product Overview

The Emerson KL3002X1-BA1 is a high-performance 8-Channel 24VDC High-Side Discrete Output Module engineered for the DeltaV M-series Distributed Control System (DCS). This module provides the necessary switching capacity to control field devices such as solenoid valves, motor starters, relays, and indicators. By utilizing a "high-side" switching architecture, the module supplies 24VDC power directly to the load while maintaining a common ground, satisfying standard safety and wiring protocols in modern process plants. It integrates seamlessly into the DeltaV I/O subsystem to deliver deterministic actuation and real-time channel feedback.

Technical Specifications

Attribute | Value
Manufacturer | Emerson Process Management
Model Number | KL3002X1-BA1
Series | DeltaV M-Series
Output Type | Discrete Output (High-Side Switching)
Number of Channels | 8 Channels
Nominal Voltage | 24 VDC
Isolation | Field-to-Logic and Channel-to-Channel Isolation
Power Consumption | Via DeltaV LocalBus (Logic) / External 24VDC (Field)
Operating Temperature | 0°C to +60°C
Dimensions | Compact Modular Card (M-series Standard)
Condition | 100% Brand New and Original

Engineering Advantages

Optimized High-Side Switching: The KL3002X1-BA1 switches the positive side of the 24VDC circuit. This design ensures that if a field wire shorts to ground, the device simply turns off or blows a fuse rather than accidentally actuating, providing a safer failure mode for critical valves and pumps.

Full Galvanic Isolation: Advanced isolation circuitry protects the DeltaV controller from field-side electrical transients and surges. This separation prevents local wiring faults from propagating back to the CPU, ensuring the integrity of the entire control network.

Hot-Swappable Maintenance: Like all M-series components, this module supports live replacement. Maintenance teams can swap a faulty module without shutting down the controller or adjacent I/O cards, drastically reducing Mean Time to Repair (MTTR).

Simplified Field Wiring: The high-side configuration allows for a common return rail for all field loads. This reduces the number of terminal block connections required in marshalling cabinets, saving labor and decreasing the complexity of the cable management system.

Integrated Diagnostics: The module provides real-time status indication for each output channel. Operators can instantly verify the state of field actuators via faceplate LEDs, allowing for rapid physical troubleshooting without software interrogation.

FAQs

Q1: Is the KL3002X1-BA1 currently in stock and brand new?

A1: Yes. We maintain a ready inventory of the KL3002X1-BA1 in 100% Brand New condition. Every unit ships in original Emerson factory packaging with a 12-month industrial warranty.

Q2: What is the benefit of a "High-Side" output vs. a "Low-Side" output?

A2: High-side outputs (like the KL3002X1-BA1) connect the load to the positive voltage source. This is the industrial standard because it prevents accidental device activation in the event of a ground fault, significantly enhancing plant safety.

Q3: Does this module require an external power supply?

A3: The logic-side electronics draw power from the DeltaV carrier. However, you must provide an external 24VDC bulk power supply to the terminal block to drive the actual field loads (solenoids, relays, etc.).

Q4: Can I use this module to replace an older VE4002 series card?

A4: The KL series is functionally compatible with many DeltaV M-series systems. However, always verify your specific DeltaV software version and the "S-series" vs "M-series" carrier requirements to ensure the firmware recognizes the module upon insertion.