FBM237R Foxboro P0914XS 8-Port Isolated Analog Interface

2026-04-13T14:07:31+08:00

Vendor: Foxboro
Type: Foxboro I/A Series
Price: 190.00

Product Overview

The Foxboro FBM237R (Part Number: P0914XS) serves as a mission-critical isolated analog output interface for Foxboro I/A Series and Evo™ distributed control systems (DCS). This module converts digital commands from the control processor into precise 0–20 mA or 4–20 mA DC signals to drive final control elements, including control valves, actuators, and positioners. With a focus on high availability, the FBM237R supports redundant pairing to eliminate single points of failure in vital process loops. We supply this module as 100% Brand New and Original, ensuring your automation infrastructure operates with factory-guaranteed precision and safety.

Technical Specifications

Feature | Specification Details
Manufacturer | Foxboro (Schneider Electric)
Model / Part Number | FBM237R / P0914XS
Output Channels | 8 Individually Isolated Channels
Output Signal Range | 0–20 mA DC (Configurable to 4–20 mA)
D/A Conversion | 13-bit Resolution
Output Accuracy | ±0.05% of Span
Isolation | Full Galvanic (Channel-to-channel and ground)
Power Consumption | 5–7 W (Typical)
Operating Temp | –20°C to +70°C
Environmental Rating | ISA Class G3 (Conformal Coated for Harsh Environments)
Housing | Rugged Extruded Aluminum

Engineering Advantages

Fault-Tolerant Redundancy: The FBM237R enables redundant module pairing. In this configuration, two modules share the same field wiring through a redundant termination assembly. If the primary module fails, the secondary unit assumes control instantaneously without bumping the output signal, maintaining stable process conditions.

Superior Galvanic Isolation: Every channel features independent galvanic isolation. This design prevents ground loops and electrical interference from migrating between channels or damaging the DCS backplane, which is essential for loops spanning large distances in refineries or power plants.

Advanced Fail-Safe Modes: The module allows engineers to configure specific behavior for communication loss. You can program each channel to "Hold Last Value" or transition to a pre-defined "Fallback" output, ensuring final control elements move to a safe state during system upsets.

EMI/RFI Shielding: The rugged extruded aluminum housing provides superior protection against electromagnetic and radio frequency interference. This physical shielding ensures signal purity in high-noise environments near heavy switchgear and variable frequency drives (VFDs).

Simplified Hot-Swap Maintenance: The module supports hot-swapping on the system baseplate. Maintenance personnel can replace a faulty unit without removing power or interrupting the operation of other FBMs, significantly reducing downtime and risk during repairs.

FAQs

How does the FBM237R handle redundant field wiring?

The FBM237R uses a specific redundant termination assembly that combines the signals from two paired modules. The software manages the "Master/Tracker" relationship, ensuring only one module drives the current loop at any given time while the other remains ready for immediate takeover.

Can I use the FBM237R for 0–20 mA devices?

Yes. While 4–20 mA is the industrial standard, the FBM237R is fully software-configurable for a 0–20 mA range, providing the flexibility needed for specialized actuators or older legacy equipment.

What is the benefit of the 13-bit resolution for valve control?

The 13-bit D/A conversion provides fine-grained control over the output current. This precision allows for very small incremental adjustments to valve positions, which improves overall process stability and reduces mechanical wear on actuators caused by signal "hunting."

Is this P0914XS unit a used or refurbished module?

No. We offer the Foxboro FBM237R P0914XS strictly as a 100% Brand New and Original product. Each unit ships in original manufacturer packaging and undergoes rigorous quality checks to meet current Schneider-Foxboro industrial standards.