KJ1501X1-BA2 Emerson | DeltaV VE5001 Process Controller

2026-04-10T10:49:35+08:00

Vendor: Emerson
Type: Process Controllers
Price: 199.00

Product Details

Product Overview

The Emerson DeltaV VE5001 (also identified by part number KJ1501X1-BA2) serves as the primary processing intelligence for the DeltaV M-series Distributed Control System (DCS). This controller executes complex control strategies, manages local I/O module communication, and facilitates data exchange with the DeltaV Control Network. By hosting the system's logic and database locally, the VE5001 ensures high-speed, deterministic control for critical process loops. It functions as the central hub of the M-series rack, providing the computational power required for modern chemical, oil and gas, and power generation automation.

Technical Specifications

Attribute | Value
Manufacturer | Emerson Process Management
Model Number | VE5001
Part Number | KJ1501X1-BA2
Series | DeltaV M-Series
Function | Central Process Controller / CPU
I/O Support | All M-series Traditional and HART I/O
Redundancy | Supports 1:1 Redundant Controller Pairs
Input Power | 24 VDC (Supplied via Carrier)
Operating Temp | 0°C to +60°C
Weight | 0.5 kg (Module only)
Shipping Weight | 2.0 kg
Condition | 100% Brand New and Original

Engineering Advantages

Deterministic Logic Execution: The VE5001 handles time-critical control algorithms with sub-second scan rates. This ensures that safety interlocks and PID loops respond instantly to field changes, maintaining stable plant operations.

Fault-Tolerant Redundancy: You can pair two VE5001 controllers in a redundant configuration. If the primary CPU encounters a hardware fault, the standby unit takes control of the I/O bus within milliseconds, preventing process upsets or emergency shutdowns.

Plug-and-Play Integration: The module utilizes the DeltaV M-series rail system for instantaneous connection to power and communication buses. This design eliminates manual wiring for the controller itself, reducing installation errors and commissioning time.

Non-Volatile Memory Protection: The onboard memory retains control strategies and current process states during power interruptions. Upon restoration, the VE5001 resumes its last known state, ensuring a safe and predictable recovery sequence.

Native Network Security: The controller communicates via the proprietary DeltaV Control Network. This architecture isolates sensitive control traffic from standard office IT networks, providing a robust layer of defense against external cyber interference.

FAQs

Q1: Is the VE5001 KJ1501X1-BA2 currently in stock?

A1: Yes. We maintain ready-to-ship inventory of the VE5001. Our standard lead time for this brand-new, factory-sealed module is typically 5 to 7 working days.

Q2: Does this controller support both digital and analog I/O modules?

A2: Yes. The VE5001 manages the full range of DeltaV M-series Traditional I/O, including 4-20mA analog, discrete 24VDC, and HART-enabled field instruments.

Q3: Can I replace a failed VE5001 without stopping the process?

A3: If your system utilizes a redundant controller pair, you can "hot-swap" the failed VE5001. The standby controller maintains the process while you insert the new module, which then automatically synchronizes its database with the active partner.

Q4: What is the warranty for the KJ1501X1-BA2?

A4: We supply this unit in 100% Brand New condition. It includes a comprehensive 12-month industrial warranty, ensuring reliable operation within your DeltaV DCS environment.